100 Amp Panel Replacement in Allentown, PA
The homeowner called due to a power outage. When we arrived, we discovered that the panel was filled with water, rust, and corrosion. We did a complete 100 Amp Service Replacement. We installed an Eaton Premium Copper Bus Main Panel, Premium Breakers, Service Entrance Cable, Meter Base and Main Grounding.